I have just installed this panel, and the GFI trips immediately when the line side is energized - with no terminations on the load side
about 50-Amp 240-Volt 240-Watt Non-Fuse Metallic Spa Panel Disconnect with GFI on
April 21, 2015
As stated, after installing this panel into an existing system that was not protected, the GFI trips immediately when the line side is energized with no terminal connections made on the load side of the GFI; I think the GFI is bad.
Answer this question
0out of 0found this question helpful.